Another satisfied customer on a Charlotte North Carolina inspection. A somewhat extensive summary on this home with a couple items of note. 1. there is an active leak underneath the kitchen with 100% moisture readings and visibly wet wood. The source of the leak was unknown. There was also some wood rot underneath bay window rear side of home. Mostly water management issues were present in crawlspace and exterior. Home was built on a hill that sloped left right leaving a low spot on the left side of crawlspace. Sump pump in this area was operational but appeared to be undersized for the amount of water that collects here. Watermarks, water on floor, water staining to foundation wall and piers, and efflorescence were widespread in the crawlspace. All these items were highlighted in the summary, and a licensed contractor will need to be called out for further evaluation and or correction of these defects.